|Place of Origin:||Assemble In Mexico|
|Minimum Order Quantity:||6sets|
|Packaging Details:||6sets packed in one carton,10kg each carton.|
|Delivery Time:||3 work-days|
|Payment Terms:||T/T, Western Union, MoneyGram|
|Supply Ability:||200sets Every Month|
|Name:||Fisher 1301F-1 High Pressure Gas Regulator||End Connetion:||1/4" NPT|
|Inlet Pressure:||6000psi(414Bar)||Outlet Pressure Range:||10-75psi(0.6-5.1bar)|
|Flow Rate:||60-90m3/h||Application:||Compression，Facilities & Process Utilities，Plant Air，Pressure Control，Wellhead|
|Body Material:||Brass||Type:||Gas Regulator|
fisher regulator valve,
fisher flow control valve,
90m3/h Fisher Gas Regulator
Fisher 1301F-1 Model Brass Body Material High Pressure Gas Regulator
Types 1301F and 1301G regulators are self-operated, high-pressure regulators, which can be used where high pressure gas must be reduced for use as pilot supply pressure in pilot-operated regulators or as loading pressure in pressure-loaded regulators. Types 1301F and 1301G regulators can also be used in many other applications as high-pressure reducing regulators for various gases.
The proven reliability and accurate regulation of the Type 1301F high pressure regulator makes it ideal for numerous high-pressure drop applications. This multi-purpose regulator can be used as pilot supply or pressure-loading regulators where high-pressure operating medium must be reduced for use by gas regulator pilots or pressure-loaded regulators. Its rugged design offers versatility for a wide variety of applications.
Type 1301F: Direct-operated high-pressure reducing regulator for inlet pressures up to 6000 psig / 414 bar and outlet pressure ranges from 10 to 225 psig / 0,69 to 15,5 bar
Body Size and End Connection Style
Maximum Inlet Pressure
6000 psig / 414 bar
Outlet Pressure Ranges
1301F-1 : 10-75psi /0.6-5.1bar
Maximum Emergency Outlet Pressure
Type 1301F: 250 psig / 17,2 bar
-20° to 180°F / -29° to 82°C
The 1301 Series regulators have an outlet pressure rating lower than their inlet pressure rating. If actual
inlet pressure can exceed the outlet pressure rating,outlet overpressure protection is necessary. However,
overpressuring any portion of the regulators beyond
the limits in Specifications section may cause leakage,damage to regulator parts, or personal injury due to
bursting of pressure-containing parts.
1301F High Pressure Regulator will suit for use on Compression,Facilities & Process Utilities,Plant Air,Pressure Control,Wellhead.
Contact Person: Barry