|Place of Origin:||Made In China|
|Minimum Order Quantity:||6sets|
|Price:||USD1780-1850 Each One Set|
|Packaging Details:||1set packed in one carton ,each carton size is 29*18*18cm,3kg/set.|
|Delivery Time:||3 work-days|
|Payment Terms:||T/T, Western Union, MoneyGram|
|Supply Ability:||500sets Every Month|
|Name:||Fisher 627H Pressure Gas Regulator Use For LPG||End Connetion:||1" NPT|
|Inlet Pressure:||2000psi/138bar||Outlet Pressure:||240-500psi|
|Body Material:||WCC||Orifice Size:||1/4"|
WCC Material Fisher Gas Regulator,
Self Operated Fisher Gas Regulator,
1" NPT Fisher Gas Regulator
WCC Steel Material Fisher Gas Regulator 627H Model Pressure Gas Regulator
Fisher Original 627H Pressure Gas Regulator
Fisher Make 627 Gas Regulator
Fisher 627 Regulator
Internal Relief Valve
Relief Operation Indicator
Easy to Maintain
Wide Range of Flow Capabilities
Fisher 627 Series self-operated pressure reducing regulators (Figure 1) are for high and low pressure systems. Fisher 627 regulators can be used with natural gas, air, or a variety of other gases. Performance characteristics vary according to construction.
The Specifications section gives some general specifications for Fisher 627 Series regulators. The nameplates (Figure 2) give detailed information for a particular regulator as it comes from the factory.
Table 1. Maximum Inlet Pressures,Outlet Pressure Ranges
|TYPE||OUTLET PRESSURE RANGE||ORIFICE SIZE,
|MAXIMUM INLET PRESSURE, PSIG (bar)|
|627||5 to 20 psig
(0.34 to 1.38 bar)
|1/2 (12.7)||250 (17.2)|
|15 to 40 psig
(1.03 to 2.76 bar)
|1/2 (12.7)||300 (20.7)|
|35 to 80 psig
(2.41 to 5.52 bar)
|1/2 (12.7)||750 (51.7)|
|70 to 150 psig
(4.83 to 10.3 bar)
|1/2 (12.7)||750 (51.7)|
1” NPT End Connection : 627-496,627-497,627-498,627-499
2” NPT End Connection:627-576,627-577,627-578,627-579
Type 627: Self-operated pressure reducing regulator equipped with a pitot tube for greater regulated capacities (Figure 7).
Type 627R: Type 627 with internal relief and with an open throat (Figure 8).
Type 627M: Type 627 with a stem seal between the body outlet pressure and diaphragm case. Pressure is measured under the diaphragm through the 1/4-inch NPT downstream control line connection (Figure 9).
Type 627MR: Type 627M with internal relief (Figure 10).
Type 627H: Type 627 with a diaphragm limiter to deliver a higher outlet pressure (Figure 11).
Type 627HM: Type 627H with a stem seal between the body outlet pressure and diaphragm case. Pressure is measured under the diaphragm through two 1/4-inch NPT downstream control line connections (Figure 12).
END Connection Sizes
1inch and 2inch
End Connection Styles
1, or 2-inch body sizes: NPT
1 or 2-inch (DN 25 or 50) body sizes:
ANSI Class 300 or 600 RF flanged
Maximum Inlet Pressure(1) (Body Rating)
2000 psig (138 bar) for NPT steel, 1480 psig
(102 bar) for RF flanged steel, or 1000 psig (69 bar) for ductile iron
Maximum Valve Disk Inlet Pressure Rating(1)
2000 psig (138 bar) for nylon disk or 1000 psig
(69 bar) for nitrile disk
Type 627, 627H or 627R: Internal
Regulator operation within ratings does not preclude the possibility of damage from debris in the lines or from external sources. A regulator should be inspected for damage periodically and after any overpressure condition. Like most regulators, 627 Series regulators have outlet pressure ratings that are lower than their inlet pressure ratings. A pressure-relieving or pressure-limiting device must be provided by the user for the Types 627, 627H, 627M, and 627HM regulators if the inlet pressure can exceed the outlet pressure rating, since these regulators do not have internal relief.
Type 627R regulators provide internal relief which limits the total outlet pressure buildup over setpoint. Use Table 3 to determine the total outlet pressure. This internal relief may be adequate for the application, if not, provide additional pressure relief or a pressure-limiting device downstream.
A regulator may vent some gas to the atmosphere. In hazardous or flammable gas service, vented gas may accumulate and cause personal injury, death, or property damage due to fire or explosion. Vent a regulator in hazardous gas service to a remote, safe location away from air intakes or any hazardous area. The vent line or stack opening must be protected against condensation or clogging.
Fisher High Pressure Gas Regulator 627H Model Stainless Steel Material Gas Regulator
Contact Person: Barry