|Place of Origin:||Assembled In China|
|Minimum Order Quantity:||2pcs|
|Packaging Details:||1set packed in one carton ,each carton size is 28*13*9cm,1.4kg each one set.|
|Delivery Time:||3-8 work-days|
|Payment Terms:||T/T, Western Union, MoneyGram|
|Supply Ability:||1000sets Every Month|
|Name:||67DFR Fisher Pressure Reducing Regulator||End Connetion:||1/2" NPT|
|Inlet Pressure:||250psi||Spring Range:||0-125psi|
|Pressure Gauge:||Can With Pressure Gauge||Micron Rating:||5 Microns|
|Maximum Emergency Outlet Pressure:||50psi|
Fisher 67DFR Instrument Supply Filter Regulator
Fisher 67DFR Filter Regulator has a filter and internal relief valve with a soft seat for reliable shutoff with no discernible leakage.
Fisher 67DFR model of regulators are typically used to deliver constant reduced pressure of gaseous fluids to pilot-operated
controllers and other pneumatic instrumentation. As shown in the Available Configurations table, an assortment of regulators
is available to meet diverse flow requirements.
|Connection Size||1/2" NPT|
|Maximum Inlet Pressure||250 psig / 17.2 bar|
|Spring Range||0-125 psi/ 0-8.6bar|
|Smart Bleed Check Valve Set point||6 psi / 0.41 bar differential|
With Nitrile (NBR):
Standard Bolting: -20 to 180°F / -29 to 82°C
With Gauges: -40 to 180°F / -40 to 82°C
Fisher 67CFR Internal Relief Performance
Low capacity for minor seat leakage only; other overpressure protection must be provided if inlet pressure can exceed the maximum pressure rating of downstream equipment or exceeds maximum outlet pressure rating of the regulator.
Smart Bleed Check Valve Set point
6 psi / 0.41 bar differential
Fisher 67CFR Filter Regulator : Filter Capabilities
Free Area: 12 times pipe area
Micron Rating: Polyethylene Filter (Standard): 5 microns Glass Fiber Filter (Optional): 5 microns PVDF or Stainless Steel Filter (Optional): 40 microns
Drain Valve and Spring Case Vent Location
Aligned with inlet standard, other positions optional
Principle of Operation
67CFR Filter Regulator Downstream pressure is registered internally on the lower side of the diaphragm. When the downstream pressure of Filter Regulator is at or above the set pressure, the valve plug is held against the orifi ce and there is no fl ow through the regulator. When demand increases, downstream pressure drops slightly allowing the spring to extend, moving the stem down and the valve plug away from the orifi ce. This allows fl ow through the regulator.
Internal Relief (Types 67CR, 67CSR, 67CFR, and 67CFSR)
If for some reason, outside of normal operating conditions, the downstream pressure exceeds the setpoint of the regulator, the force created by the downstream pressure will lift the diaphragm until the diaphragm is lifted off the relief seat. This allows flow through the token relief. The relief valve on the Type 67CR, 67CSR, 67CFR, or 67CFSR is an elastomer plug that prevents leakage of air from the downstream to atmosphere during normal operation, thereby conserving plant air.
Smart Bleed Airset
In some cases, it is desired to exhaust downstream pressure if inlet pressure is lost or drops below the setpoint of the regulator. For example, if the regulator is installed on equipment that at times has no flow demand but is expected to backflow on loss of inlet pressure. The Types 67CFR and 67CFSR can be ordered with the Smart Bleed option which includes an internal check valve for this application. During operation, if inlet pressure is lost, or decreases below the setpoint of the regulator, the downstream pressure will back flow upstream through the regulator and check valve. This option eliminates the need for a fixed bleed downstream of the regulator, thereby conserving plant air.
The 67C Series filter regulators have maximum outlet pressure ratings that are lower than their maximum inlet pressure ratings. A pressure relieving or pressure limiting device is needed if inlet pressure can exceed the maximum outlet pressure rating.
Types 67CR, 67CSR, 67CFR, and 67CFSR have a low capacity internal relief valve for minor seat leakage only. Other overpressure protection must be provided if the maximum inlet pressure can exceed the maximum pressure rating of the downstream equipment or exceeds the maximum outlet pressure rating of the regulator.
Contact Person: Barry